I have a company in town that warehouses paper. They are interested in housing and distributing alcohol-based hand sanitizer. Where can I find the proper code for needed sprinkler load for alcohol-based hand sanitizers?
The NFPA 13 Annex , 5.6 directs you to Chapter 22 for flammable liquids and alcohol based products that contain over 20% alcohol. Ch. 22 entitled Special Occupancy Requirements, 22.2.1 references NFPA 30 as the document for fire protection criteria. You may find what your looking for in Chapter 16 in the 2015 edition.